Top Plant: Isogo Thermal Power Station Unit 2, Yokohama, Japan*
Posted by imambudiraharjo on June 14, 2011
By Dr. Robert Peltier, PE (POWER’s editor-in-chief)
Unit 2 at J-POWER’s Isogo Thermal Power Station entered commercial service in July 2009. The 600-MW ultrasupercritical unit joins an earlier, similar plant built in 2002. Together, these two new plants replaced 1960s-vintage coal-fired plants and doubled power generation from the small project site. In addition, the new unit improves the plant’s gross thermal efficiency to about 45% while reducing air emissions to those of a gas-fired combined-cycle plant.
J-POWER was established as a wholesale power generator and wires company by the Japanese government in 1952 and was privatized in 2004. Today, J-POWER is owned by Electric Power Development Co., Ltd. (EPDC), which continues to distribute wholesale energy from principally hydroelectric and fossil-fueled plants to 10 utilities located across Japan.
The original Isogo Thermal Power Station (Isogo) consisted of two coal-fired units, each rated at 265 MW, that began commercial operation in 1967 and 1969. After 35 years of service, J-POWER elected to repower the plant, which is located on a peninsula in Yokohama Harbor. The project had three goals: The new plant was to lower emissions levels to those of a gas-fired plant, increase the amount of electricity produced for Japan’s second-largest city, and improve the plant’s operating efficiency.
Build, Scrap, Build
Development of the new facilities on a tight 30-acre site used what EPDC called the “build, scrap, build” approach. First, the new 600-MW Unit 1 was built; then the older two units were shut down and scrapped to free up precious land; then the new 600-MW Unit 2 was built. This approach also ensured that the new Unit 1 reliably replaced the energy produced by the old plant before decommissioning.
Construction of the new Isogo Unit 1 began in 1998, and commercial operations followed in April 2002. The two older units were decommissioned in November 2001, and the project site was “scrapped” by March 2004. Construction of the new Unit 2 began in October 2005, and it entered commercial service in July 2009.
When Isogo Unit 2 entered commercial service, power generating capacity was more than double what had been produced by the original plant. In addition to meeting Yokohama’s generation needs, Isogo was designed for maximum thermal efficiency.
High efficiency requires high steam pressures and temperatures. The main steam pressure is ultrasupercritical (USC) at 25 MPa (3,626 psi) with a main steam temperature of 600C (1,112F). Reheat is a blistering 620C (1,148F). Unit 1 operates with the same steam conditions, except the reheat temperature is just 10C less, at 610 C. The gross thermal efficiency of the new Unit 2 is 45% (LHV).
Isogo ranks as the cleanest coal-fired power plant in the world in terms of emissions intensity, with levels comparable to those from a natural gas–fired combined-cycle plant. The air quality control system on Unit 2 is a multipollutant control system, unlike the individual components found on Unit 1 and on most coal-fired plants. Unit 2 uses a unique regenerative activated coke dry-type technology (ReACT) that scrubs SOx from the flue gas but also removes mercury and NOx as a co-benefit (Figure 1). A thorough discussion of this new multipollutant control technology appeared in “ReACT Reduces Emissions and Water Use” in the July issue of POWER, which can be accessed at http://www.powermag.com.
Figure 1. World-class performance.
In the ReACT multipollutant control system, flue gas passes through activated carbon in the desulfurization tower to adsorb sulfur oxides. Spent activated carbon is sent to the regeneration tower, where the SO2 is removed and the activated carbon is reused. The SO2 is recovered as a highly concentrated sulfuric acid that has market value. As a co-benefit, 20% to 40% of the NOx and up to 90% of both elemental and oxidized forms of mercury are removed in the process. Courtesy: J-POWER
Another very important advantage for the ReACT technology is that it uses only 1% of the water required by conventional wet flue gas desulfurization systems.
The low levels of air emissions reached by Isogo Unit 2 are, quite frankly, phenomenal and set a new standard for coal-fired power plant design that should interest plant designers and regulators alike:
- Flue gas emissions are first treated by an ammonia selective catalytic reduction de-NOx system before entering the ReACT system. Together, they reduce NOx from 159 ppm to an average of about 16.5 ppm (13 ppm is the permit level for Unit 2). However, operating experience has found that the plant typically operates in the single-digit ppm levels. This equates to an overall NOx removal rate of about 92%.
- ReACT reduces SOx from 60 ppm to an average of 15 ppm (10 ppm is the permit level for Unit 2). Unit 2 regularly operates with single-digit ppm levels of SO2, reflecting an almost 98% rate of reduction.
- ReACT removes up to 90% of both elemental and oxidized forms of mercury through adsorption using activated coke.
- By using an electrostatic precipitator, soot and dust emissions were reduced from 50 mg/Nm3 to an average of 7.5 mg/Nm3, and Unit 2 operates at less than 5 mg/Nm3 or 0.005 lb/mmBtu). This performance equates to over 99.9% removal efficiency. The flue gases are then exhausted to the atmosphere through a common 200-m stack.
- The improved plant thermal efficiency reduced the amount of CO2 released into the atmosphere by 17% on a lb/kWh basis. J-POWER understands that reducing CO2 reductions from coal-fired plants begins by designing a plant with the highest possible thermal efficiency.
Strong Market Plant
Demonstrated single-digit levels of emissions could have a profound impact on future permitting of coal-fired plants worldwide, especially in the U.S. Certainly, constructing a similar plant in the U.S. would set the benchmark for emissions permits for future coal-fired plants.
J-POWER has also announced that “preparations for environmental impact assessment” have begun for replacement of the two units at the Takehara Thermal Power Station. This 1,300-MW station, built in 1967 and 1974, would remain in service during construction of two like-sized, but much more efficient units with much lower emissions. The two older units would be retired after construction is completed in 2020. Construction is estimated to begin in 2014.